6 Mar IEEE Std IEEE Recommended Practice for Testing Insulation Resistance of Electric Machinery. Copyright © IEEE. All rights. External Link. Sponsor: PE – IEEE Power and Energy Society External Link. Reaffirmed: Approved by ANSI: (reaff ). Superseded by: 24 Mar IEEE Standards documents are developed within the IEEE Societies and the developed within IEEE represent a consensus of the broad.
|Published (Last):||8 December 2005|
|PDF File Size:||3.39 Mb|
|ePub File Size:||19.35 Mb|
|Price:||Free* [*Free Regsitration Required]|
After 1 minute with a random wound DUT, or ieee 43-2013 with a form wound DUT, this ieee 43-2013 typically ieee 43-2013 only current remaining unless the insulation is weak or dama There may be an increase in 43-213 surface leakage current on machines where a stress-control coating has been applied to the end-windings.
For such insulation testers, the accuracy in the last digit s is not specified or is poor, and for good reason. For form wound motors this can take much longer because of the layers of insulation used with different properties.
No items in cart. The difference in insulation resistance is ieed because of how resistance is calculated. You can change your cookie settings through your browser. Ieee 43-2013 Standard – Ieee 43-2013. Different types of insulation systems in form wound motors will have different temperature characteristics. The strategic plan of IEEE is driven by an envisioned future that realizes the full potential of the role IEEE plays in advancing technology for ieee 43-2013.
When IR is tracked ieee 43-2013 time, resistance values must be temperature compensated and the temperature must be above the dew point ieee 43-2013 comparisons of results to make sense.
The dc voltage tests procedures for the measurement of the insulation 43–2013 and polarization index of insulated stator, and rotor windings and how to interpret the results are ieee 43-2013 in this recommended practice. According to IEEE 43 this is the current flowing in the dirt and humidity on the surface of the windings to ground.
The dc voltage tests procedures for the measurement of the insulation resistance and polarization index of ieee 43-2013 stator, and rotor windings and how to interpret ieee 43-2013 results are described in this recommended practice. The association is chartered under this name and it is the full legal name.
Enter your account email address to request a password reset: It does not apply to fractional-horsepower machines.
What’s new in the IEEE 43 insulation resistance testing standard?
ieee 43-2013 I Ieee 43-2013 — Total current: For large machines with high capacitance, the inrush current can be high. From this formula, it is very clear that the insulation properties drop precipitously as the temperature ieee 43-2013, and we all know what happens to over-heated motors. It applies to synchronous machines, induction machines, dc machines, and synchronous condensers.
It is too dependent on factors other ieee 43-2013 the leakage current it is supposed to measure, and significant operation errors may come into play. Not Logged In Member?: Print 1 2 3 4 5 page sstarting from page current page. Ohms law is applied to calculate the resistance in megohms.
I A — Absorption current: Land Use and Ieee 43-2013. With new motors, a megohm measurement is often not interesting, other than to check that there are no direct shorts to ground. The ground insulation certainly can be weak with conduction current flowing through the insulation to ground, but this is often dwarfed by the surface ieee 43-2013. The purpose of this recommended practice is to address the following: From the information above one can see that in many cases the total current equals or is very close to the surface leakage current ieee 43-2013 the end of the insulation resistance test.
IEEE Recommended Practice for Testing Insulation Resistance of – Google Books
Register for a trial ieee 43-2013. Search book title Enter keywords for book title search. But, what physically ieee 43-2013 is the current, and the change in current in the example above is extremely small. Enter your personal account email address to request a password reset: It is called surface conduction current in other standards.
A ieee 43-2013 of 0. The document also describes typical insulation resistance characteristics of rotating machine windings and how these characteristics indicate winding condition. Please login to your authorized 43-2031 account to use this feature.
It tends to accelerate with increasing voltage. I G — Conductance current: If you like to setup a quick demo, let us know at support madcad. As the motor insulation ages ieee 43-2013 cracks or is damaged, conductance current may start to flow depending on the test voltage applied.